On November 16, 2016, a sprinkler head unexpectedly activated in a duct within the plant laboratory. After it was determined that there was no fire hazard, the water supply was isolated and the activated head was replaced. Observation of the sprinkler head revealed that the two arms of the sprinkler head had severed midway between the base and the deflector. When installing fire sprinkler heads in corrosive environments, special attention should be paid to the chemicals that the sprinkler head will be exposed to. Sprinkler head manufacturers offer a variety of studies and advise to aid the design engineer in matching the appropriate sprinkler head to the environment it protects.
You are accessing a U.S. Government information system.
Unauthorized or improper use or access of this system may result in disciplinary action, as well as civil and criminal penalties.
By using this information system, you understand and consent to the following:
You have no reasonable expectation of privacy when you use this information system; this includes any communications or data transiting,
stored on or traveling to or from this information system. At any time, and for any lawful government purpose, the government may monitor,
intercept, search and seize any communication or data transiting, stored on or traveling to or from this information system.
The government may disclose or use any communications or data transiting, stored on or traveling to or from this information system for any lawful government purpose.
Classified or Official Use Only information is not allowed on this website.
Need help? Contact the System Administrator 509-376-4821 or
OPEXShare@rl.gov. Their hours of operation are 6 AM to 4 PM PT Monday through Thursday.