While troubleshooting the loss of power in cubicles at PNNL's new 3860 Building in March, electricians discovered an energized power distribution assembly (PDA) in recently installed cubicle partitions. The subcontractor tasked with this work scope, which was a change to the original scope, ran out of parts during the installation; there were not enough receptacles and cover plates available to shield the energized components. The subcontractor assumed it was acceptable to leave them uncovered and energized until additional parts were available.
Lessons Learned: Recognize that scope changes or additions, no matter how minor, may invite additional risk. Provide adequate oversight of work performed by subcontractors, who may not be knowledgeable on PNNL's requirements. Consult equipment manufacturer's instructions to assure hazards are recognized and controlled.
You are accessing a U.S. Government information system.
Unauthorized or improper use or access of this system may result in disciplinary action, as well as civil and criminal penalties.
By using this information system, you understand and consent to the following:
You have no reasonable expectation of privacy when you use this information system; this includes any communications or data transiting,
stored on or traveling to or from this information system. At any time, and for any lawful government purpose, the government may monitor,
intercept, search and seize any communication or data transiting, stored on or traveling to or from this information system.
The government may disclose or use any communications or data transiting, stored on or traveling to or from this information system for any lawful government purpose.
Classified or Official Use Only information is not allowed on this website.
Need help? Contact the System Administrator 509-376-4821 or
email@example.com. Their hours of operation are 6 AM to 4 PM PT Monday through Thursday.