Power Operators at the Radiochemical Processing Laboratory were performing efficiency testing of High Efficiency Particulate Air filters in the facilitys ventilation system using a "hot" aerosol generator when smoke and oil vapor at the discharge port created a small flame. The Power Operators disconnected the electrical supply and smothered the flame. The System Engineer paused work and called 375-2400 to report the event. No emergency response was required, no one was hurt, and the fire was confined to the aerosol generator. The flame was likely ignited after the generator was moved to check and refill the oil reservoir, although it is designed to run for four hours without needing a refill. Lessons Learned: A pre-job was held but the Preventative Maintenance package did not cover the safety guidelines contained in the generator operators manual related to the potential fire hazard. The Power Operators were required to read the operators manual. Assure workers are trained adequately on the equipment they are operating and that they understand the manufacturers instructions and warnings.
You are accessing a U.S. Government information system.
Unauthorized or improper use or access of this system may result in disciplinary action, as well as civil and criminal penalties.
By using this information system, you understand and consent to the following:
You have no reasonable expectation of privacy when you use this information system; this includes any communications or data transiting,
stored on or traveling to or from this information system. At any time, and for any lawful government purpose, the government may monitor,
intercept, search and seize any communication or data transiting, stored on or traveling to or from this information system.
The government may disclose or use any communications or data transiting, stored on or traveling to or from this information system for any lawful government purpose.
Classified or Official Use Only information is not allowed on this website.
Need help? Contact the System Administrator 509-376-4821 or
OPEXShare@rl.gov. Their hours of operation are 6 AM to 4 PM PT Monday through Thursday.