Type: Just-In-Time Report
Publisher: CH2MHill Plateau Remediation Company (Richland, WA - Hanford Site), Richland, WA - Hanford Site (CHPRC)
Published As: Public
At this time, the electricians observed the 480 volt energized line side bus bar for the main disconnect was accessible in the cubicle next to where they had removed the panels. There was no barrier between their work area and the bussing going into the line side of the main disconnect (a separation panel was not in place). The electricians immediately backed away from the panel and notified supervision. If they had continued, electricians would have been working in close proximity to exposed hazardous electrical energy.
You must be logged in to open the attachment.Download Article