Type: Lessons Learned
Publisher: CH2MHill Plateau Remediation Company, Hanford Site (CHPRC)
Published As: Public
Lesson Learned: Control panels (and instrument panels) are complex and often contain multiple electrical components requiring additional rigor when determining, reviewing, and approving a lockout/tagout electrical isolation boundary. All drawings should be reviewed and qualified electricians should be involved in identifying isolation boundaries.
You must be logged in to open the attachment.Download Article