The early onset of the cold weather without freeze protection fully installed led to freezing of the process system piping. This condition caused failures of numerous components such as valves, fittings, instrument sensing lines, etc. Furthermore, additional damage resulted from the loss of heater(s) main power during a lower temperature period. With one heater to the main liquid processing facility powered by a diesel generator the temperatures plummeted in the process area resulting in additional freeze out and component damage.
You are accessing a U.S. Government information system.
Unauthorized or improper use or access of this system may result in disciplinary action, as well as civil and criminal penalties.
By using this information system, you understand and consent to the following:
You have no reasonable expectation of privacy when you use this information system; this includes any communications or data transiting,
stored on or traveling to or from this information system. At any time, and for any lawful government purpose, the government may monitor,
intercept, search and seize any communication or data transiting, stored on or traveling to or from this information system.
The government may disclose or use any communications or data transiting, stored on or traveling to or from this information system for any lawful government purpose.
Classified or Official Use Only information is not allowed on this website.
Need help? Contact the System Administrator 509-376-4821 or
firstname.lastname@example.org. Their hours of operation are 6 AM to 4 PM PT Monday through Thursday.