A Los Alamos National Laboratory pipefitter sustained a burn injury to his left ankle when he was sprayed with scalding water while performing blow down activities on a boiler. Boiler operators were in the process of blowing down a boiler that had unexpectedly shut down during the weekend and had been restarted on the following Monday morning. The boiler was in a cold state and had to be drained prior to restart. The low drain valve was opened to drain the boiler and was inadvertently left in the open position on Monday morning. On Monday afternoon, boiler operators attempted to perform the required blow down operation. As the pipefitter actuated a fast acting valve and began opening a slow acting gate valve, hot water at a temperature of 320 degrees from the low point drain valve located at floor level was discharged directly towards the pipefitters foot/ankle and resulted in a seconddegree burn to the ankle. The pipefitter was able to close the fast action valve and subsequently closed the slow action valve to stop the flow of hot water.
Lessons Learned Workers should verify the valve configuration(s) of boiler/steamcondensate systems prior to start-up or troubleshooting operations to identify drain pipe openings that can potentially expose them to injury from the inadvertent flow of hot water, steam or condensation. Work control documents or operating procedures that relate to pressure systems must specifically address these configuration control hazards and controls.
You are accessing a U.S. Government information system.
Unauthorized or improper use or access of this system may result in disciplinary action, as well as civil and criminal penalties.
By using this information system, you understand and consent to the following:
You have no reasonable expectation of privacy when you use this information system; this includes any communications or data transiting,
stored on or traveling to or from this information system. At any time, and for any lawful government purpose, the government may monitor,
intercept, search and seize any communication or data transiting, stored on or traveling to or from this information system.
The government may disclose or use any communications or data transiting, stored on or traveling to or from this information system for any lawful government purpose.
Classified or Official Use Only information is not allowed on this website.
Need help? Contact the System Administrator 509-376-4821 or
email@example.com. Their hours of operation are 6 AM to 4 PM PT Monday through Thursday.